The importance of an attic ventilation system cannot be overemphasized. Ventilation is the most efficient way to remove heat and moisture from an attic space. Proper design and installation of roof vents can make your home more comfortable and prevent a number of roof problems. There are a wide variety of roof vents that are designed to work in conjunction with one another to achieve the required amount of ventilation for most houses.
Why do attics need to be ventilated?
- Attics that are properly ventilated allow hot air to exhaust from the attic in the summer. The chart above illustrates the advantages of a well ventilated attic system. Hot air can infiltrate the living space as the attic temperature increases. This makes living conditions uncomfortable and requires the cooling system to work harder. The increased attic temperature also causes greater thermal expansion of the shingles and roof deck. This is a problem that will be discussed in greater detail in regards to the shingle manufacturer's warranty.
- Properly ventilated attics allow warm and humid air to exhaust in the winter. Warm air that is trapped in the attic in the winter months can cause several problems, including condensation and ice dams. Condensation occurs when the moist air from inside the house (often from bathroom vents) comes in contact with the cold attic air. Condensation can cause the damage to the insulation, wood framing, wood roof deck, and drywall. Ice dams can be prevented by proper attic ventilation. For details on the causes and effects of ice dams, click here.
- The life of the roof is extended if the attic is properly ventilated. Most shingle manufacturers require proper ventilation to validate the shingle warranty. It is not uncommon for an unventilated roof system to fail after only ten years. Thermal expansion (and contraction) of the shingles and roof deck is the major cause. Higher attic temperatures increase the rate of thermal expansion for the shingles. The shingles that are exposed to higher rates of expansion tend to weaken around the fasteners and the adhesive strips. When the roof deck is exposed to higher temperatures, the resulting thermal expansion can cause the shingles to buckle.
It is worth noting that the adhesives strips that bond the shingles together at the laps have greatly improved over the past decade. The primary benefit of improving the adhesive or sealant strip is to increase a roof system's resistance to high winds. Ten years ago, common shingles were rated to withstand winds of 60 MPH. In comparison, the Owens Corning 30 Year Duration shingles are presently rated for a wind resistance of 110 MPH. Since these shingles have greater bonding strength, high rates of thermal expansion cause more tension at the shingle sealant strip than it would have a decade ago. Therefore, the importance of decreasing thermal expansion through ventilation is more important today than it was in the past.
Types of Roof Vents
A balanced attic ventilation will consist of two types of roof vent:
- Air Intake or Soffit Vents (which unfortunately do not exist on some houses)
- Air Exhaust Vents
The amount of air that flows through the vent is called the Net Free Vent Area or NFVA.
If Intake or soffit vents have been installed on a house, they can be found on the lower part of the roof system. The four main types of intake vents are continuous soffit vents, rectangular soffit vents, vented vinyl soffit, and specialty intake vents. Continuous soffit vents are the most desirable. A minimum of 50% of the NFVA should be installed as intake vents, if possible. Intake vents should be installed with air baffles which prevent attic insulation from blocking the airflow. It is important to make sure your soffit vents are unobstructed for them to function properly. To do this, look in your attic on a sunny day — if you can see daylight coming in through the vents, your intake vents were properly installed.
Exhaust vents are always installed near the ridge or upper part of the roof system. There are many types of roof exhaust vents, including continuous ridge vents, louvers or 750 vents, gable vents, and power vents. The selection of the exhaust vent is a very important consideration that is usually determined by the architectural style of the house. For homes with good intake ventilation, a continuous ridge vent is usually the best choice. The Owens Corning VentSure continuous ridge vent system allows 20 inches of NFVA per foot, making it one of the most efficient ridge vents on the market today.
How the Vents Work
Builders, Architects, and Roofing Contractors should always try to design a balanced system of intake and exhaust vents. Hot air accumulates in the attic when the sun radiates on the surface of the roof. The hot attic air rises and exhausts through the vents at the upper portion of the roof, creating a suction or negative pressure in the attic. The negative pressure at the exhaust vents causes the cooler outside air to be pulled in through the soffit vents. This process is called natural convection.
Soffit vents do not exist in many homes, even though they are the most important component of a roof ventilation system. The process of natural convection is not efficient if soffit vents are not installed or installed improperly. The following scenario is a demonstration of the convection process with and without soffit vents:
The air intake will always occur at the path of least resistance. When soffit vents are not installed the path of least resistance can come from interior spaces such as attic or wall penetrations. The most common areas that enable air to escape into the attic include light fixtures, electrical outlets, and heating and cooling ducts. When air is pulled out of the living space and into the attic, the heating and cooling system is required to work harder and the energy efficiency is decreased.
The process of forced convection occurs when a power vent is installed in the attic. In Cincinnati, it is important to install a power vent with a humidistat and thermostat setting. A power vent such as the Lomanco Model 2000H has settings to automatically start the fan when the temperature is above 90 degrees F. or relative humidity is above 40%. The power vent is designed to depressurize the attic space by exhausting warm or moist air and replace it with cool, dry air (from the soffit vents). Power vents can also pull air out of the living space if soffit vents are not installed or installed improperly. Power vents are the best choice for most hip roofs since the ridge area is too small to achieve the required NFVA by using a ridge vent or louvers.
Common Problems with Roof Vents
Individuals with an understanding of roof ventilation systems can go to great lengths to design a balance of intake and exhaust and the correct combination of roof vents. Unfortunately, it is not uncommon to see roof vents improperly installed. Many homes that were constructed during the housing boom (of the past decade) had serious problems, including problems with the ventilation system. Here are a few examples:
Designing the Right System
Many older houses have unusual attic spaces that were designed before the movement towards greater energy efficiency had begun. A balance of intake and exhaust ventilation can be very challenging on these types of projects and requires an expert design. Homes that were constructed without intake vents are one of these unusual projects and will be discussed later.
The Asphalt Roofing Manufacturers Association or ARMA outlines three simple steps to properly ventilate an attic space.
- Calculate the square footage of the attic floor.
- Determine the placement of the intake and exhaust vents.
- Calculate the NFVA for each vent.
ARMA recommends a NFVA of 1 square foot for every 300 square feet of attic floor space if both intake and exhaust vents are installed. A typical home with an attic floor space of 2000 square feet will require the 480 square inches of intake vents and 480 square inches of exhaust vents. These calculations were determined by using the 1:300 ratio as follows:
- 2000 Sq Ft of attic floor space = 288,000 square inches of attic floor space (2000 x 144)
- 288,000 Sq inches/ 300 sq inches = 960 square inches of NFVA required
- Since it is our goal to achieve a balanced system, 960 / 2 = 480 square inches of both intake and exhaust vents should be installed.
The rectangular soffit vents and the continuous ridge vent are commonly combined to provide a balanced system of intake and exhaust. In the case of the 2000 sq ft attic floor space, a minimum of 18 rectangular soffit vents should be installed (with 28 square inches of NFVA each) and 24 Feet of ridge vent (with 20 inches of NFVA per foot).
The Chart below documents the number of roof vents required in order to achieve a balanced system.
Houses without Soffit Area
The architectural style of some houses makes it is very difficult to achieve a balanced ventilation system. Victorian and Cape Cod houses usually have insulation that is blocking the airflow from the soffit area to the exhaust vents. Removing or decreasing the thermal barrier (insulation) in order to achieve better ventilation is not recommended. For more information on how to ventilate these types of homes click here.
Some houses are constructed without a soffit overhang . A customer can choose from the following four options to improve their ventilation on this type of house:
- Install a Vented Fascia Board. The Vented Fascia Board was designed and patented by Deer Park Roofing, Inc. in order to provide intake ventilation on houses with no overhang. The Vented Fascia Board is manufactured by Crane Roofing Products Ltd and provides 9 inches of NFVA per Foot.
- Install a Smart Vent. The smart vent can be added during a new roof installation. It usually requires attic baffles to be installed on the interior of the attic space as well. For more information on the smart vent, click here.
- Install gable vents that can provide air intake. This option is not available to all homeowners - depending on the architectural style of the house.
- Double the amount of exhaust. The 1:300 ratio is changed to the 1:150 ratio in this case. Many homeowners choose this option because it is the least expensive of the four.
Competent design and installation is the key to maximizing the performance of your attic ventilation.
A Deer Park Roofing Staff member can inspect your house to determine any necessary improvements. You can request an estimate online or email us for more information.